This heavy-duty commercial door has a full thermal break and is pre-hung with 2 way swing capability. It consists of a 16-gauge steel jamb and a 24 gauge insulated steel panel. Three heavy duty stainless steel, fixed pin hinges are included. Low-E glass is recommended when adding a lite kit, this will ensure premium energy efficiency. A handicap approved threshold and a header are also included. An embossed six-panel or cross-buck design are available in bone white.
Polar White Bronze Hickory Moss
3/0 x 6/8 3/6 x 6/8 4/0 x 6/8 Dbl. 6/0 x 6/8 3/0 x 7/0 3/6 x 7/0 4/0 x 7/0
6/0 x 6/8, 7/0 x 6/8, 8/0 x 6/8, 6/0 x 7/0, 7/0 x 7/0, 8/0 x 7/0
Out-to-out 3/0 x 6/8 frame size is 39 ¾” x 82 ⅛". (Rough Opening 40 ¼” W x 82 ½” H)
Double doors have a removable mullion centered in the frame of the pair - shipped knockeddown.
Hinges are attached to jambs. Manual head and foot bolt concealed in the mullion.
(3) 4 ½” x 4 ½” Stainless Steel NRP (non-removable pin) high quality hinges are standard.
Smooth 24 gauge galvanized steel painted finish. 3068 available in 6-panel or X-Buck styles
Rolled formed edge interlocked in thermally broken aluminum core rails. (Patented assembly)
HDPE lock reinforcing structure, optional steel plate closer & panic hardware blocking.
Optional full hardware installation. Special lock blocking is available
Flush Panel R-13 injected polyurethane core (u= .077)
3/0 x 6/8 only - Six panel (6P) style, X-Buck (XB) style
Polar White, Chocolate Brown, Hickory Moss or Bronze finish paint
Standard with 2 ⅛” lockset bore, 2 ¾” backset. Non-bored is optional
Standard edge prep for deadbolt. Interconnected lock prep is available
Durable Alcryn bulb & fin sweep.
1 LB-2 22x36 no grids 9 LB-2 22x36 9 lite grids
1 LG-2 22x30 no grids used with exit panic bar 1 LE-2 16x16 no grids
9 LG-2 22x30 9 lite grids used with exit panic bar 1 LK-2 30x36 12 lite grids used with 4068/4070
1 LI-2 20x24 no grids 1 LC-2 7x60 no grids
15 L-2 22x60 15 lite grids 1 LL -2 22x60 no grids
Other glass sizes are available. All glass is tempered and labeled per test criteria CPSC 16 CFR
Part 1201 Cat. II.